Generator Sizing and Compatibility for Uninterruptible Power Supplies
Most critical power protection solutions, incorporating uninterruptible power supplies (UPS), today are interfaced with an alternative source of back-up power (standby power) which could be a fuel cell or flywheel but more usually it is a diesel generator. Generator sizing and UPS compatibility are fundamental to power continuity and must be taken into account at the outset of any power protection plan.
A generator must be sized correctly so that when it's required to do so it will be able to power the UPS (taking into account any allowance for harmonics that the UPS's rectifier will generate) and the load/s that the UPS is supplying. Generators are typically rated in two ways:
Prime Power Rating (PPR) - whereby the generator supplies power as an alternative to the mains power supply, but on an unlimited basis.
Standby Power Rating (SPR) - whereby the generator supplies power as an alternative to the mains power supply but for a short duration, typically one hour out of every twelve.
A generator rated under SPR can be as much as 10 percent larger than one sized using PPR. This provides an overload capability for a short duration, perhaps to meet sudden load demand changes, for example.
For an uninterruptible power supply installation, PPR is the more suitable method of rating. It is extremely important, for achieving greater resilience (fault tolerance), that a generator and its UPS are suitably matched. Not only must a generator be able to accept the load of the uninterruptible power supply but the UPS rectifier and static bypass supplies must be able to operate with, and synchronise to, the output of the generator.
Generator set manufacturers have four recognised categories of load acceptance: one = 100%, two = 80%, three = 60% and four = 24%. Categories two, three and four are used in practice for PPR-rated generators. Load acceptance is closely related to the turbo charging system and the Break Mean Effective Pressure (BMEP) of the engine. This is a function of engine speed, number of cylinders and the swept volume of each cylinder.
For load acceptance to occur, a UPS must be able to synchronise to the voltage waveform supplied by the generator. Uninterruptible power supplies tend to have fairly wide input voltage windows and generator output is usually well within this. Its frequency, however, can vary, which can be problematic. This is overcome by widening the UPS operating parameters to accept a broader range. This may not always be sufficient, particularly for poorly maintained or undersized generators. Their output frequencies could drift and make it impossible for the UPS to synchronise.
A generator can never be matched on a 1:1 aspect ratio with an uninterruptible power supply. A UPS will at times be drawing additional current to charge its battery set. Generator sizing may also have to take into account the powering of essential loads, air-conditioning, for example, and emergency lighting. As already mentioned, a UPS rectifier can generate harmonics and this needs also be the taken into consideration when sizing the generator.
The ambient temperature around a generator is important. It is usual for the engine room temperature to rise by around 10 degrees centigrade when a generator is in operation. Things can get quite hot if the outside temperature is also hot. High ambient temperatures can degrade generator performance and cause damage to turbo-chargers and exhaust systems. In such instances, it is normal to de-rate and increase the overall size of the generator installation.
Recommended practice is to oversize a generator by a factor of one-and-a-quarter to two-times the size of the uninterruptible power supply and to increase this to three-times or more when additional essential loads are to be powered.
Related Tags: generators, uninterruptible power supplies, power protection, riello ups, standby power
Robin Koffler is the General Manager for Riello UPS Ltd the UK subsidiary of Riello UPS (RPS S.p.A) a leading European manufacturer of Uninterruptible Power Supplies and a co-author of The Power Protection Guide(ISBN 978-0-9554428-0-3)- available from Amazon.comYour Article Search Directory : Find in Articles
Recent articles in this category:
- Offshore it Consulting Services India
Cost effectiveness of productions offers a cutting edge in this age of stiff competition. Lower is
- Geeks Who?
Geeks are characterized by the tools they use. What all one should have to qualify to be called gee
- Now Wi-fi (vi-fi) in Vehicles
This is a Wi-Fi age. Those who need can find Wi-Fi hotspots everywhere; in home, hotels, airport lo
- How Web Development Can Catalyze Your Profit Prospective?
Website is the heart and soul of an online business. It depicts the appearance of your products, se
- Free Cisco Ccna, Ccnp, Ccent Tutorial on Switching, Spanning-tree Protocol (stp)
A Layer 2 switch, which functions as a transparent bridge, offers no additional links for redundanc
- Windows Vista Sidebar, Gadgets, Easy Wireless Networking and Improved Back Features
Microsoft has tried to put "active" items on the Windows desktop for nearly a decade. Finally, with
- Windows Vista Features and Upgrading the Windows Vista Versions
Microsoft Windows Vista is the latest workstation version of the Windows operating system and is de
- Comptia A+, Network+ Certification Tutorial - Function of Network Hubs
A hub is a device used to connect all of the computers on a star or ring network. A hub is nothing
- Tips for Unlock Iphone 3G
Anybody who owns an iPhone wants to have it unlocked and they need unlock iPhone 3G tips, in genera
- Unlock Iphone Tutorial
Most of the people consider that it is difficult to unlock iPhone, but in fact, this process is eas
Most viewed articles in this category:
- It Consulting - Buyer Fraud Prevention
Hiring the wrong computer consultant is not only frustrating, but it can also leave you cheated of y
- San Francisco Web Design and Web Development Services
A San Francisco Web Development and Web Design Services, #10 offers a full range of marketing and we
- Complex Issues, Comprehensive Solutions by Freelance Providers
As business increases, customers are most certainly asking for their share of higher business value,
- Gaming and Graphic Design Computer Monitor Solutions
CRT screens are fast moving towards obsolescence and are now almost the preserve of Graphic designer
- Help Wanted - One New Customer for Growing IT Business
Your computer services business is the same, you need customers. But do you need as many as you thin
- What Does it Take to be a Top IT Manager Today
Well-Run Concepts has been conducting research on how we can quantify what personal skills or compet
- What Are Hosted Applications?
As access to the Internet becomes more widespread with faster, more reliable and 'always on' connect
- Password Security
In the past I've never really paid much attention to security issues when it comes to user names and
- General Computer Maintenance For The Masses
Reorganizing the file systemGo to “Start” > “Run” > Type in “def
- How Does Human Resource Management in the Workspace Effect Me?
How often do you find yourself saying: "I wish I knew how to learn more about this topic" Well, w